Tampa ESD Flooring Installation
Tampa ESD Flooring
- Comination Electrical Resistance Technician, Heel Straps and ESD Floor Testing per ANSI/ESD
STM97.1(note: passing is less than 1.0E09)
- Environmental Conditions 48.2% rH, 68.4 degrees F.
- Minimum 9.52E05
- Maximum 6.32E06
- Median 3.03E06
- Average 3.23E06
Our first ESD flooring Installation for Tampa Microwave was over two
years ago. The ElectraGuard ESD Epoxy Flooring has held up very well
at the original site. Hence, it was the material of choice for their
new facility comprising of 3 areas similar in size to the room shown
below with a total size of roughly 75,000 square feet. This
installation was complicated due to the remnants from internal walls
that had been fastened to the concrete.
All of the holes were meticulously filled and the concrete was
diamond ground to an SP2 profile prior to the application of 3 coats
of ElectraGuard, 2 coats of ElectraThane Sealer and a sacrificial
top coat of ElectraSheen Sapphire II for ultimate ease of
maintenance and durability.